Control, automation and tele-management via 10 logical outputs (relays) and 10 logical inputs
Via Internet in real time. 24 / 7 / 365.
Programmable control of relays (10 relays) with level alarms in time-slot (multiple permutations of programmable sequences), independent programmable notices via e-mail of all measurement alarms, etc.
Alarm centre, automation and tele-management via 10 logical outputs (relays) and 10 logical inputs.
Programmable enablement of each relay (10 relays) upon:
Locking of diferencial I / o locking of MCB I / o locking of intensity and / or overvoltage and / or low voltage and / or MCB and / or intensity and / or differential intensity and / or neutral intensity and / or power factor and / or voltage THD and / or intensity THD and / or voltage unbalance and / or intensity unbalance and / or manual OFF via front panel or via Internet and / or over-temperature and / or low temperature and / or over-humidity and / or low humidity and / or over-frequency and / or low frequency and / or phase sequence and / or Remote input 1 and / or Remote input 2 and / or time programmer and / or timer 1 and / or 2 and / or 3 and / or 4 of módule 1, and / or timer 1 and / or 2 and / or 3 and / or 4 of módule 2.
Programmable and time-delay enablement of each output relay (4 Relays for module 1 and 4 Relays for module 2) and 8 direct inputs at 230V AC:
Module 1: Timer 1, Timer 2, Timer 3, Timer 4.
Module 2: Timer 1, Timer 2, Timer 3, Timer 4.
Remote inputs 1 and 2, programmable signal-action:
Programmable input signal, normal or to-fro, with programmable unlocking option and reclosure reset upon enablement.
Time programmer with high-precision clock:
6 programs per day which permit enablement of any relay (10 relays) or the MCB with programming in hours and minutes.
Up to 10 output and 8 input relays:
10 output relays with manual control and associable to alarms, time-delay inputs, time programmer and DataWatchPro software. 8 input relays associable to enablement of 4 timers, DataWatchPro software.
Programmable, independent start-up delays:
Due to power failure or to voltage cut-off, frequency, voltage THD or voltage unbalance.
Programmable, individual sequential reclosures for:
Intensity, I (0-10 reclosures). RCD (0-30 reclosures), MCB (0-10 reclosures). Likewise, neutral intensity or power factor or intensity THD or intensity unbalance (0-10 reclosures).